The transformer works with transformer oil. The transformer oil is placed in the transformer box, just like the oil in the tank of a tricycle. Transformer oil in the position in the work and production of transformer is relatively high, transformer oil itself is transformer operation of raw materials, thus protect the transformer oil, transformer oil is transformer properly run a necessary condition. The position of transformer oil in the tank can also be measured, and there are strict limits on this standard, which cannot be too high or too low. However, there are many cases where the oil level of transformer oil is too high. What causes the high oil level of transformer oil? How to deal with such problems?
北京11选5开奖结果查询Reasons for high transformer oil level:
1. The change of transformer temperature can change the oil level. With the change of oil temperature, oil level also appears correspondingly -- the change of fixed range. However, under abnormal conditions, abnormal changes in oil level may also occur due to oil seepage, water seepage and other faults.
北京11选5开奖结果查询2. Secondly, the change of oil temperature is related to load condition, environment temperature and other conditions. When oil level change is inconsistent with these factors, it may be false oil level. Reasons for the false oil level: a. B. The explosion-proof pipe vent is blocked.
北京11选5开奖结果查询3. In addition, excessive oil level will cause oil spill.
北京11选5开奖结果查询Treatment and emergency measures:
北京11选5开奖结果查询1. If there is gas relay protection, the trip circuit shall be removed to prevent accidental trip.
北京11选5开奖结果查询2. The operator of the electrical equipment in the shift shall check the oil level indicator frequently, and if the oil level is too high, oil can be released appropriately;
北京11选5开奖结果查询3. When abnormal injection of oil is found in the oil pillow or explosion proof pipe, the power of the transformer should be cut off immediately to prevent the failure and expansion of the accident.
PREV：How to choose the "companion" of transformer -- transformer distributor
NEXT：What items should be inspected before the transformer leaves the factory
Copyright © 2018 All Rights Reserved ： Jiangsu Zheng Wei Electric Power Equipment Co., Ltd.